DOL(Direct online starter)
At the starting instant,a 3-phase induction motor acts as a poly phase Transformer having an air gap with a short-circuited secondary.If the motor of higher capacity(larger than 2 kW) is connected directly to the supply mains,it will draw heavy current(about 5-8 times the rated full-load current) at the starting instant which is offensive because it will cause large voltage drop in the distribution network and thus affect adversely the operation of other electrical equipment connected to the same distribution network.Hence,to control the starting current,use of starter is essential for starting of 3-phase induction motors of larger size(rating exceeding 2 kW).
Starter used for starting of a squirrel cage induction motor are:
- Direct-on-line starter
- Line resistance starter
- Star-delta starter and
- Auto- transformer starter
DOL Diagram and working principle
Squirrel cage motors of capacity up to 1.5 kW,double cage motors and squirrel cage motors of large capacity having a large rotor resistance are started by DOL method.This is one of the most economical method of starting of induction motors.
This method involves the direct switching of poly phase squirrel cage induction motor to the supply mains.In this method of starting of cage motors the rate of temperature rises is high and the motor may get damaged if the starting period is large which may be due to
- excessive load
- insufficient rotor resistance or
- excessive voltage drop in the supply mains
The starting period usually lasts a few seconds because starting torque for induction motor is about twice the full-load torque.
DOL starter wiring Diagram
The above shown is the push button type direct-on-line starter which is very common in use.This type of starter is simple,inexpensive and easy to install and maintain.It consists of set of `start` and
`stop` push buttons,a contractor(an electromagnet) with its associated contacts and usually an overload and under voltage protection devices.
The start button is momentary contact switch that is held normally open by a spring.The stop button is held normally closed by a spring.When a start button is pressed the operating coil(or main contractor) gets energized through the overload relay contacts OL(normally closed).This closes the three main contacts M that connects the motor to the supply.At the same time a set of auxiliary or maintaining contacts MC are closed.When the maintaining contacts MC are closed,a new circuit is established through stop button,maintaining contacts MC and operating coil.since operating coil circuit is now maintained by the auxiliary contacts MC,the start button may be released.When the stop button is pressed,the operating coil gets de-energized,thereby opening all main contacts and auxiliary contacts.
The main contacts and the maintaining contacts gets opened when the supply fails or line voltage drops a certain value.When the supply gets return,the contractor cannot close until the start button is again closed. contractor is controlled by a three-wire control circuit which maintains the interruption of the circuit even after the supply is restored,this is the under voltage protection for the motor.
Overload protection is employed for protecting the motor and control apparatus from excessive heating due to overloads on motor.
Thermal overload relays are commonly used for motor overload protection.Thermal overload relays are of two types.Both types are operated from the heat generated in a thermal element through which the motor current flows.In one type, the heat bends a bimetallic strip and in the other the heat melts a film of solder.Both act to open the motor control circuit and disconnect the motor from the source of supply.
A bimetallic strip is made of two different metals whose surface has been welded together.one of the metal expands rapidly as compared to the other,when heated.When heat is applied,the strip is caused to deflect or curl up due to unequal expansion of the two metals.When the motor current attains a predetermined value,the heat generated deflects the strip far enough to trip a latch that opens the motor control circuit.When the strips cools down sufficiently,the relay may be reset and the motor re-started.
In case of solder film type of overload relay the heat generated at a given overload current melts the film,which releases a latch arrangement and opens the motor control circuit.When the solder has cooled enough to hold the latch,the relay may be reset.
In case of thermal relay,the time required to operate is determined by the magnitude of current flowing in the heater.Thus ,the relay operates slowly for light overloads but disconnects the motor in a short time for dangerously heavy overloads. Relays in which the time of operation is inversely proportional to the amount of current flowing are known as the inverse time relays.
Torque Developed on Starting of Induction Motor By Direct switching
where I2 is the rotor current per phase,R2 is rotor resistance per phase,T is the torque developed,s is the slip and w is the supply angular velocity.
Since rotor current is proportional to stator current I1,so
At starting slip,s=1
so starting torque,
when the motor is connected directly across the supply mains,the starting current is equal to the short-circuit current,Isc.
Advantages of DOL starter
- Simple,inexpensive and easy to install and maintain.
- Full starting torque at starting.
- DOL starter connects the supply to the delta winding of the motor.
Disadvantages of DOL starter
- Starting current is about 5-8 times of full load current.
- This method is suitable for only small machine as there is significant voltage dip.
- Unnecessary high starting torque.
- Mechanically tough.
DOL starter Applications
- Used in small water pumps.
- conveyors belts
- fans and compressor
For more notes on Electrical Engineering: